Turbomiser chillers slash cooling energy use at a data centre
Published: 01 December, 2011
Energy savings of 55% have been achieved following the replacement of existing cooling plant with new Turbomiser chillers at the west London data centre of Colt Technology. The new chillers have also improved reliability and reduced maintenance costs.
Colt Data Centre Services asked Cool-Therm to provide a turnkey package, matching the existing cooling load of the data centre and maintaining cooling at all times during the changeover.
Six chillers were installed, and Cool-Therm advised that the most efficient method of operation would be to run them all together under inverter control, at the same time maximising condenser efficiency by using all the heat-exchanger surfaces to reject heat.
Operating efficiency was also improved by increasing the flow/return chilled-water temperatures from 6/12°C to 8/14°C.
A monitoring system was installed to compare energy consumption against the previous system.
Guy Ruddock, VP operations for Colt Data Centre Services, comments, ‘The energy-efficiency expertise and experience gained is now being applied across the Colt estate by local teams.’For more information on this story, click here: December 2011, 80
- 16 - 18 February, 2016ACR Show
- 22 February, 2016Light for life: human-centric lighting (free event)
- 24 February, 2016, 18:00 - 23 March, 2016Daikin UK to help engineers ‘Mind the performance gap’ at Future Thinking seminars
- 25 February, 2016ESTA's 14th annual aM&T conference and exhibition
- 29 February - 03 March, 2016BIM Masterclasses
- 01 March, 2016Heat metering for the Renewable Heat Incentive (RHI)
- 08 - 10 March, 2016Ecobuild
- 17 March, 2016Smart Energy Marketplace
- 19 April, 2016The future of facilities management and property services in the public sector
- 04 May, 2016, 9:30 - 05 May, 2016All-Energy
- 12 May, 2016BCIA Awards
- 25 - 26 May, 2016LIFTEX 2016
- 17 June, 2016CSA Awards
- 08 - 09 September, 2016Zero carbon buildings today and in the future